GREENSTAR 24I JUNIOR MANUAL PDF
Boiler Manuals for the Worcester Greenstar 24I Junior NG appliance. View and Download Worcester GREENSTAR 24i junior instruction manual online . wall hung RSF gas-fired condensing combination boiler installation. View and Download Worcester GREENSTAR 24i junior instruction manual online . WALL HUNG RSF GAS FIRED CONDENSING COMBINATION BOILER.
|Published (Last):||23 April 2006|
|PDF File Size:||8.47 Mb|
|ePub File Size:||20.24 Mb|
|Price:||Free* [*Free Regsitration Required]|
The addition of sealing agents to the system water is not recommended as this can cause problems with deposits left in the heat exchanger.
Wall mounted combination boiler for central heating and mains fed domestic hot water 36 pages. Ensure tube outlet B is These are not polarity sensitive.
Got it, continue to print. Replace expansion vessel and refit the boiler to the mounting frame. After cutting, the end must be square and free from burrs to prevent damage to the mm flue seals.
Worcester Greenstar 12i System Instruction Manual 74 pages. Log in or Register.
Worcester GREENSTAR 24i junior Instruction Manual
For short periods the built-in frost protection of the appliance will be adequate. Page 15 Number, Date of Installation. Remove template F and wall mounting frame E from the packaging. To reset press and mahual the reset button E for 2 seconds. C over the notches to secure.
Boiler Manuals: Worcester Greenstar 24I Junior NG
Is the incoming gas pressure at least 18mbar with the boiler at maximum output? Page 40 Remove stainless steel viewing mirror F. Page 50 To refit, follow the above in reverse. Connect the gas supply to the boiler gas manal 22mm compression. It will be necessary to run water through the DHW circuit to ensure that the boiler will not cycle on low heating demands. Don’t show me this message again.
UK Call Centre Tel. E upwards and slide the control support bracket F to the left. If the burner fails to light after 5 attempts the electricity supply to the gas valve will be interrupted. Remove clamping plate K. Connect froststat cables to terminals FS and FR.
The inner sleeve B opens as shown. In such circumstances, the advice of the local water authority should be sought. This allows the heating system and mains water connec- tions to be filled and checked prior to boiler installation.
Never terminate or discharge into any open source, including; sink, bath, shower, bidet, toilet etc. Further guidance on pipe routing can be found printed on the boiler template supplied with the boiler. Lift up assembly and remove from boiler.
Worcester 28i Junior LPG. Flue Terminal Positions This could be a nuisance, for example, near security lighting. That Worcester Heat Systems material charges and free of labour Limited will not accept charges by Worcester Heat Systems responsibility for damage caused by Limited.
Mxnual do I release pressure so red needle is set at 1half to 2 as at moment its 4. Enter text from picture: Book an engineer, pay bills, join Rewards and more Access your account. Boiler Connections F from the retaining bracket.
Hang the boiler on to the wall mounting frame by the two brackets positioned left and right at the top rear of the appliance. To print the manual completely, please, download it. Wall hung rsf gas fired condensing combination boiler 20 pages. Wall mounted combination boiler for central heating and mains fed domestic hot water 36 pages. Wall mounted combination boilers for central heating and mains fed domestic hot water 65 pages.
Table Of Contents L. This kit can be used in conjunction with the optional filling loop 7 not sup- plied with the boiler. Isolate gas supply at boiler gas cock.
Vent any air from the boiler heat exchanger using a suitable container to collect any water N. Remove bottom panel by pulling it forward and off. Pump head Ensure the boiler is fully drained see draining the appliance. Remove clamping plate L.